Don’t forget to perform grounding. The boiler has two terminals prepared for the connection of the thermostat ambient (see wiring diagram), which should remove the jumper that links terminals 3-4 and then connect the room thermostat. Installation of the burner boiler Granada can be supplied with a support of Domestic diesel burner. For installation in the boiler, follow these instructions:-remove the side cover of home heating oil. -Cut with a blade the ceramic fibre that covers the hole where the barrel of the burner should go. -For the installation of fuel meets the instructions enclosed with the burner. -The boiler has two terminals 5 6 for the electrical connection of the burner. Mounting of the draught regulator for mounting damper supplied with the boiler, must meet the following instructions:-with the boiler empty and cold, screw the regulator into the hole prepared for it in the boiler, until you achieve a perfect seal.
-Insert the hexagonal lever through the side hole by moving the plastic tube and directing it slightly above the horizontal plane. -Slide the lever so not difficult to open or close the door of the boiler load. -Fix the lever with the screw so that it does not shine into one of their flat sides. -Switch on the boiler and wait until water temperature reaches on the thermometer operating setpoint. -Then turn the selector knob to match the temperature of red color scale that indicates the thermometer. -With the hatch closed air main entrance to join the chain to this and let it taut. INSTALLATION filling installation filling should be performed slowly to allow air from the installation, through the trap installed in the boiler.
Likewise, the rest of the installation by using the traps laid down therein must be purged conveniently. Once full installation, close the filling valve. Note: Switch on the boiler without water may cause serious damage to the same.